Refrigerant liquid from a sump in the condenser (No. 24 in Fig. 8-11) is subcooled by passage through a line in the cooler (No. 27 in Fig. 8-11). The refrigerant then flows externally through a strainer and variable orifice (No. … Continue reading →
10. January 2011 by admin
Categories: Condensers |
Tags: Motor-Cooling Cycle |
Leave a comment
© 2020 HVAC Troubleshooting. Theme: Ari by Elmastudio. Proudly powered by WordPress.