AHU – Preheat Coil
The preheat coil should have wide fin spacing, be accessible for easy cleaning, and be protected by filters. If the preheat coil is located in the minimum outdoor airstream rather than in the mixed airstream as shown in Figure 1, it should not heat the air to an exit temperature above 2 to 7°C; preferably, it should become inoperative at outdoor temperatures of 7°C. Inner distributing tube or integral face and bypass coils are preferable with steam. Hot water preheat coils should have a constant flow recirculating pump and should be piped for parallel flow so that the coldest air will contact the warmest part of the coil surface first.
Categories: Air Distribution | Leave a comment